IEC 60099-5 PDF
IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Genre:||Health and Food|
|Published (Last):||18 February 2014|
|PDF File Size:||1.58 Mb|
|ePub File Size:||7.87 Mb|
|Price:||Free* [*Free Regsitration Required]|
Surge protective devices, and 37B: The way these transmission-line choices will improve or degrade lightning performance is also provided. This ieec constitutes a technical revision. Metal-oxide surge arresters with external series gap EGLA for overhead transmission and distribution lines of a.
Contact us svenska Login.
BS EN 60099-5:2013
Protective equipment for series capacitor banks This part of IEC covers protective equipment for series capacitor banks, with a size larger than 10 Mvar per phase. Subscribe on standards with our subscription service.
Selection and application recommendations. Glossary of terms and definitions from IEC publications,, and This standard provides a list of terms and definitions relative to IEC publications from IEC technical committee Valid Buy this standard.
These are surge arresters consisting of one or more non-linear resistors which may be in series with single or multiple spark gaps. This website isc best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3.
Copyright – ArresterWorks.
The Redline version is not an official document, it is available in Iwc only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition. Learn more about the cookies we use and how to change your settings.
It covers phase-to-phase, phase-to-earth and longitudinal insulation 6009-95 three-phase systems with nominal voltages above 1kV Preview Insulation co-ordination – Part 4: In many cases, the prescribed steps are adequate.
The recommendations for the capacitor part are given in IEC Selection and application recommendations Status: This guide recognizes that a perfect line design does not exist, and that a series of compromises are made in any distribution-line design.
They are not used in general to provide surge protection. The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued. Computational guide to insulation co-ordination and modeling of electrical networks This technical iex gives guidance on conducting insulation co-ordination studies which propose internationally recognized recommendations for the numerical modeling of electrical systems including arresters and for the implementation of deterministic and probabilistic 600999-5 adapted to the use of numerical programs.
IEC Surge Arresters: These are protective devices mainly 660099-5 in fixed installations of d.
IEC RLV | IEC Webstore
When you use our service you can be assured the latest editions and easy access. Surge arresters containing both series and parallel gapped structures – Rated 52 kV and less This standard applies to all metal-oxide surge arresters with gaps and housed in either porcelain or polymeric housings.
September Replaced By: Selection and application recommendations Article no: Do you need a multi-user copy? You may find similar items within these categories by selecting from the choices below:.
Our prices are in Swiss francs CHF.
Surge arresters – Part 5: Selection and application recommendations
More complex and special solutions requiring study by experienced engineers is described, but specific solutions are not always given.
The guide does not cover motors applied in solid-state switched adjustable speed drives. The procedures are based on theoretical studies, test idc, and experience. Part 5 Selection and application recommendations This standard provides recommendations for the selection and application of surge arresters to be used in three-phase systems with nominal voltages above 1kV.
This standard applies to devices for separate mounting and to devices supplied integrally with other equipment.